Pay attention to WeChat public number
Factory Address: Zhuzhuyuan Industrial Development Zone, Xindu District, Chengdu, Sichuan Province
Sales Department Address: 3103, Fulin Building, No. 388 Shuanglin Road, Chenghua District, Chengdu, Sichuan Province
Tel: +86-28-84369578 +86-28-84364618 +86-28-84388516
COPYRIGHT©Chengdu Huayi Heat Shrinkable Products Co., Ltd All rights reserved.
Heat shrinkable cable accessory installation precautions
The parts of the heat-shrinkable cable accessories that are in contact with the metal parts (such as lead packages and terminals) should be carefully roughened and cleaned with a cleaning agent. At the end of the cable end, the core should be prevented from being displaced to avoid affecting the sealing effect. During the construction process, it is strictly forbidden to damage the cable sheath and insulation. The heat-shrinkable intermediate connector is not allowed to move the cable when it is not completely cooled. The above are the installation conditions and installation requirements for the heat shrinkable cable accessory products.
The heat shrinkable cable accessory has the characteristics of small size, light weight, convenient carrying and convenient installation. During the installation of the heat shrinkable cable accessories, the ambient temperature should be above 0 °C and the relative humidity should be below 70%. Avoid condensation on the insulation surface, and take remedial measures when the ambient temperature is low and the humidity is too high. Be careful not to cut the heat shrink tube at will. It is not possible to construct in rainy and foggy weather. If the cable is found to be ingress or damp, remedial measures should be taken.